said by KCrimson:
The ground in your picture is visibly attached to that metal pipe/conduit - does anyone know if its up to NY's spec?
As long as that is the elec. feed to the meter(as it appears to be ) it is up to spec. If that were a conduit coming from the breaker panel it wouldn't be.