O Fallon, MO
|reply to sk1939 |
Re: Wiring Behind 70's Panelboard
They are probably confused. On 20A and below circuits, you can FMC as the equipment grounding conductor. Over 6', and you have to include an actual EGC.
In some cities, they don't allow flex over 6' period, and only allow it for fixture whips.
This goes back to the earlier thread with cities / municipalities adding their own little quirks.
I wouldn't use flex, as it's a pain in the ass. If you are allowed to use MC or AC, I would use that instead.
...because I care.