|reply to cowboyro |
Re: Smaller size wire on 20A circuit for dedicated purpose?
Simple and direct answer, NO...
Stop and think about it. The light fixture wires will never be carrying a load other than the light fixture. The wire from the breaker to the bathroom will be carrying multiple loads that will add up.