|reply to alkizmo |
Re: Bare ground need conduit ??
You ain't just whistlin' Dixie brother--I've only Skimmed it (not yet Studied it) and so far all I've gotten out of it is that you can't count on Earth Ground for a "return path", and (I think) also that while it Used To Be that a remote building didn't need a ground rod, now it is recommended to have a ground rod In Addition to a ground Conductor/Wire back to the service panel.
Gonna read it again (and again) but it does make my brain hurt...