how-to block ads
|reply to peasoup42 |
Re: Goodman furnace doesn't stay lit
Now that we have an idea what the problem is, I "fixed" your original chronology of events.Had a Lennox that did this, but I believe that we had to replace the entire inducer motor assembly. What is happening is that when the blower comes on, it pressurizes the system and that is causing a fault in one of the pressure sensors. In other words, the pressure is correct with the inducer motor but not when the blower starts.
said by robbin:Actually, the sequence I had was what it was doing. I had let it go a couple of cycles to make sure what was happening. But TY for double-checking me.
Now that we have an idea what the problem is, I "fixed" your original chronology of events.