Howard City, MI
|reply to mepadre |
Re: Sump Pump - Discharge riser freezing
move back up valve and or redesign to allow for stand of water after valve in pipe that is is warm part of system only- maintain zero water in cold area. Any other design means you need to add heat.
in short put valve closer to pump and eliminate a long run of water in pipe in colder part of system.